My house currant comes from a step down transformer attached to the low end legs on the 440 system. Apparently the transformer exspired so was replaced with another one. The currcet tests hot until you throw the breakers then it displays nothing yet the supply in wires still test hot, what the .............?? Suggestions, answers??